The warm air inside your home is drawn into the system through return ducts and then go over a refrigerant coil. As the warm air is blown across the cooled coil, heat is removed. Refrigerant lines then carry the heat outside. Now you’re left with cool, comfortable indoor air that you can enjoy on the hottest of days. And that’s pretty much it. Sure, the equipment is more complex than that, but the process itself is easy to break down and comprehend.
As this liquid passes through the indoor cooling coil on the inside of the heat exchanger, two things happen to the air that passes over the coil’s surface on the outside of the heat exchanger. The air’s temperature is lowered (sensible cooling) and moisture in the air is removed (latent cooling) if the indoor air dew point is higher than the temperature of the coil’s surface. The total cooling (capacity) of an AC system is the sum of the sensible and latent cooling. Many factors influence the cooling capacity of a DX air conditioner. Total cooling is inversely proportional to outdoor temperature. As the outdoor temperature increases the total capacity is reduced. Air flow over the indoor cooling coil also affects the coil’s capacity and is directly proportional to the total capacity of an AC system. As air flow increases, the total capacity also increases. At higher air flow rates the latent capacity of the cooling coil is reduced. Indoor temperature and humidity also affect the total capacity of the AC system. As indoor temperatures increase, the sensible capacity also increases. Similarly, as indoor relative humidity increases the latent capacity of the AC system increases. Manufacturers of AC equipment typically provide a “performance map” of specific equipment to show how total, sensible, and latent capacity change with changing indoor and outdoor temperatures and humidity. Power consumption and energy efficiency are also provided in these charts.
The most common type of central air conditioning is the split system, which features a large, boxy condenser outside the home and a fan-and-coil system inside, connected by pipes carrying refrigerant. The air is distributed through ductwork. However, not every home can accommodate the ductwork needed to install central air. Split ductless systems are an option for those homes because, as the name indicates, they don’t require ductwork.
Keep in mind that ducts used for heating might not be the right size or in the right location for optimal cooling. Your contractor should ensure that duct sections are properly sized and that there are enough supply registers to deliver sufficient air to the right spots. Undersized ductwork can make for inefficient and noisy operation. Here’s how to keep yours humming:
Air Conditioning Your home's air conditioner is an essential part of your overall indoor comfort. A properly working system can mean the difference between a cool, comfortable summer and a hot, miserable few months. If you're currently dealing with a broken air conditioner, an inefficient system, or you would like to schedule a routine, pre-season tune-up, Horizon Services is here to help!
For more than sixty years, Nerthling's Heating and Air Conditioning has continued a tradition of superior customer service across Erie County, including Erie, Millcreek and Fairview. Family owned and operated, we treat you, your home, and your comfort the way we would like to be treated. This commitment to integrity extends to every service and product we provide. Our goal is to deliver the highest rewards for your investment, whether you require installation, maintenance, or repair. We offer a wide range of styles and sizes of equipment, services, and resources to help you achieve your goals for temperature control, air quality, and energy savings.
Typically found in induced draft furnaces, an intermittent pilot ignites the burner gas with a high-voltage spark only when the thermostat calls for heat. Once the pilot is lit, and the main burner senses the pilot flame (using a flame sensing rod), the main burner ignites. The intermittent pilot flame goes out after the heating cycle and remains off until the next time the thermostat calls for heat.
HVAC is an important part of residential structures such as single family homes, apartment buildings, hotels and senior living facilities, medium to large industrial and office buildings such as skyscrapers and hospitals, on ships and submarines, and in marine environments, where safe and healthy building conditions are regulated with respect to temperature and humidity, using fresh air from outdoors.
Contact/Relay -- Relays are electronically controlled switches that activate the various components of your HVAC system. They manage everything from the power going to the motor to automatic dampers, humidifiers, etc. Most of them are controlled by the thermostat. The most common failure for a relay is being stuck in the "open" position. Separated from its assigned contact point, it fails to complete the connection and send the message to whatever it was supposed to operate. This failure usually occurs from use over time. Each time a relay connects and sends its signal, the electrical arcing from point to point eventually causes wear and tear.
Compressor -- Compressors are outdoor components in your system. The compressor is the pump that circulates the refrigerants through the air-conditioner. You can hear it when it's running so you'll know if it's working just by listening. If it starts getting louder, your compressor is about to fail. If it makes no sound when it should be on, it has already failed. Compressors fail for a number of reasons. Most often they fail due to strain from another failed part such as the fan motor. Electrical storms can also damage compressors. If the sound from the compressor gets louder or if you see a decrease in performance, you should have your compressor checked. A failed compressor will not heat or cool your house.
Has another company told you that your furnace has a cracked heat exchanger? The heat exchanger is the heart of your furnace. Its failure can result in a dangerous situation for your home and the best solution is usually a new furnace. Because of these issues, Bonney takes this situation very seriously. We will offer you proof of the cracked heat exchanger in the form of a picture from our video inspection camera or a report from our exhaust gas analyzer, before we make our recommendation.
A packaged system is a single unit combining all the components described in the split system. Since the unit is a package, it must be placed outside the building and indoor air is “ducted” from the building to the packaged system and back through an air distribution system. These units typically have SEER rating from 10 to 18. If heating is required, an alternate method of heating the interior of the building must be used, usually in the form of electric or gas heating.