As this liquid passes through the indoor cooling coil on the inside of the heat exchanger, two things happen to the air that passes over the coil’s surface on the outside of the heat exchanger. The air’s temperature is lowered (sensible cooling) and moisture in the air is removed (latent cooling) if the indoor air dew point is higher than the temperature of the coil’s surface. The total cooling (capacity) of an AC system is the sum of the sensible and latent cooling. Many factors influence the cooling capacity of a DX air conditioner. Total cooling is inversely proportional to outdoor temperature. As the outdoor temperature increases the total capacity is reduced. Air flow over the indoor cooling coil also affects the coil’s capacity and is directly proportional to the total capacity of an AC system. As air flow increases, the total capacity also increases. At higher air flow rates the latent capacity of the cooling coil is reduced. Indoor temperature and humidity also affect the total capacity of the AC system. As indoor temperatures increase, the sensible capacity also increases. Similarly, as indoor relative humidity increases the latent capacity of the AC system increases. Manufacturers of AC equipment typically provide a “performance map” of specific equipment to show how total, sensible, and latent capacity change with changing indoor and outdoor temperatures and humidity. Power consumption and energy efficiency are also provided in these charts.
We are service professionals! As licensed contractors and specialists in the field of heating and air conditioning, we have the tools, the equipment, and the experience to keep your equipment running smoothly all year long. If it is emergency service that you need we are available to assist you! To help reduce service emergencies, we offer service agreements to keep your comfort system running at peak performance.
If you find yourself with a need today, don’t hesitate to contact us now. We want to prove to you why we have such stellar ratings for quality and customer satisfaction in Cary. To easily make an appointment, you can contact us on our website, chat online, or call us at 919-578-4329. With one conversation, we’ll show you why you can be comfortable and confident in your decision to work with us. Find out today what your friends and neighbors in Cary have already found: You can rely on Service Experts.
In 1758, Benjamin Franklin and John Hadley, a chemistry professor at Cambridge University, conducted an experiment to explore the principle of evaporation as a means to rapidly cool an object. Franklin and Hadley confirmed that evaporation of highly volatile liquids (such as alcohol and ether) could be used to drive down the temperature of an object past the freezing point of water. They conducted their experiment with the bulb of a mercury thermometer as their object and with a bellows used to speed up the evaporation. They lowered the temperature of the thermometer bulb down to −14 °C (7 °F) while the ambient temperature was 18 °C (64 °F). Franklin noted that, soon after they passed the freezing point of water 0 °C (32 °F), a thin film of ice formed on the surface of the thermometer's bulb and that the ice mass was about 6 mm (1⁄4 in) thick when they stopped the experiment upon reaching −14 °C (7 °F). Franklin concluded: "From this experiment one may see the possibility of freezing a man to death on a warm summer's day."
Multiple inventions within this time frame preceded the beginnings of first comfort air conditioning system, which was designed in 1902 by Alfred Wolff (Cooper, 2003) for the New York Stock Exchange, while Willis Carrier equipped the Sacketts-Wilhems Printing Company with the process AC unit the same year. Coyne College was the first school to offer HVAC training in 1899.
HVAC is an important part of residential structures such as single family homes, apartment buildings, hotels and senior living facilities, medium to large industrial and office buildings such as skyscrapers and hospitals, on ships and submarines, and in marine environments, where safe and healthy building conditions are regulated with respect to temperature and humidity, using fresh air from outdoors.